Earlier this week, the FCC’s Enforcement Bureau released an Order approving a consent decree with Scripps Broadcasting where Scripps agreed to pay a penalty of $1,130,000 for perceived violations of the FCC’s rules requiring tower light monitoring for towers used by a number of TV stations that it had recently purchased. The company also agreed to adopt numerous procedures to insure continuing compliance, including notification to the FCC of future issues. The FCC began the investigation when a plane crashed into one station’s tower. While the FCC specifically states that it did not find any evidence that any of the “irregularities” in the tower monitoring process contributed to the plane crash, the crash opened the door to the FCC’s investigation of the company’s tower light monitoring process at all of its stations, leading to this fine. Are you ready for such an investigation?
In the consent decree, the Commission cites various tower-related FCC rules that must be observed by tower owners. The rules include Section 17.47(a), which requires antenna structure owners to monitor the status of a structure’s lighting system by either (1) making “an observation of the antenna structure’s lights at least once each 24 hours either visually or by observing an automatic properly maintained indicator designed to register any failure of such lights” or (2) by “provid[ing] and properly maintain[ing] an automatic alarm system designed to detect any failure of such lights and to provide indication of such failure to the owner.” That rule also requires that the tower owner inspect any automatic monitoring system at least once every 3 months to make sure that it is working correctly, unless the owner is using a system certified as reliable and not requiring such inspection by the Wireless Bureau of the FCC (see our articles here and here where FCC fines were issued when monitoring systems did not alert the tower owner of tower lighting issues).
Continue Reading FCC Consent Decree Requires $1,130,000 Payment to Settle Issues About Monitoring Tower Lights – Are You Doing What’s Required?